Payment & Shipping Terms:
|Material:||Cold Rolled Steel Plate||Applications:||Rack Mountable Cabinet In Data Center|
|Connector Capacity:||144 Pcs SC||Connector Type:||Connector Type: SC/APC|
|Model Number::||KXT-U-01-4U||Application:||Major Applied In Branch Connection Of Optical Cable Termination|
4U 144 Core Rack Fiber Optic Patch Panel
KXT-U-01 series optical fiber terminal box can be applied in the branch connection of fiber termination,working as distribution box,19’’standard structure,rack mounting,available for the installation of FC,SC,ST,LC adaptors.
The product can be used on the terminal of the optical cables, different types and structures, the diameter of which are within 18mm(f) tray.
1. All property indexes are in accordance with National YD/T925—1997 Standard.
2. The body make use of cold rolling steel sheet Strong adhesive force, artistic and durable.
3. Distinctive design of 1-2 cable entrance and fiber exit of 1-48 cores assures flexibility.
4. Cable entrance are sealed with oil resistance NBR to increase the flexibility. Users can choose to prick the entrance and exit.
5. Overlapping fiber-melting tray and separate insulation earth unit make the disposition of the cores, expanding the capacity and cable-earthen flexible, convenient and safe.
Main technical Specifications:
|3||optical fiber winding radius||≥40mm|
|4||extra loss of fiber tray||none|
|5||fiber length left in tray||≥1.6m|
|6||fiber capacity||144 cores|
|7||working temperature||-400C ~ + 600C|
|10||Material||Cold-rolled steel sheet|
|12||Max capacity||144 SC|
1. Peel the cable , take off the outer and inner housing, as well as loose contract tube, and wash off the filling grease, leaving 1.1～1.6m fiber and 20～40mm steel core.
2. Fix the cable-pressing card and the cable, as well as the cable reinforce steel core.
3. Lead the fiber into the melting and connecting tray, fix heat contract tube and melted tube to one of the connecting fiber. After melting and connecting the fiber, move heat contract tube and melted tube and fix the stainless (or quartz) reinforce core stick ,make sure the connecting point is in the middle of the housing pipe. Heat the pipe to make the two into one.Put the protected joint into the fiber-laying tray.(one tray can lay 12 cores)
4. Lay the left fiber in the melting and connecting tray evenly, and fix the winding fiber with nylon ties. Use the trays from the bottom up. After all the fiber has been connected, cover the top layer and fix it.
5. Position it and use the earth wire in accordance with the project plan.
1. terminal case main body: 1 piece
2. polishing sand cloth: 1 pcs
3. melting and connecting mark: 1 pcs
4. heat shrinkable sleeve: 2～24 pcs
5. tie: 4～24 pcs
1.Good reply: Your inquiry related to our products or price will be replied within 24 hours.
2.OEM&ODM: We can help you to design or put your logo and company name into products.
3.Remote Technical support&Full Technical Document
4.Warranty: 1 year warranty( While the warranty is not responsible for those broken by violence or updated with other brands.)
5.English software, English Indicator
6.Professional, Very competitive price
7.Large Stock, Fast Delivery