Payment & Shipping Terms:
|Colour:||Gray||Core Number:||16 Core|
|Into Cable Size:||2.0~12.5mm||Out Cable Size:||2.0 3.0 4.2 4.6 4.8 Mm|
16 Core Fiber Optic Distribution Box Gray PC+ABS+PE Splitter and Fiber Splicing 1×16 Wall Hanging Pole Installation
Small size and light weight for easy installation compact body
·Wall mounted with mechanical protection function
·Available for FC,SC,ST,LC adatpers
·Fiber can get in from bottom or side
·Anti-UV, Ultra violet resistant and rainfall resistant
|Out Cable diameter(mm)||0.9 , 2.0 , 3.0 , 4.2 , 4.8|
|Max capacity of splice||16|
1, Environmental requirement
2, Main technical datasheet
UPC return loss:≥50dB
APC return loss:≥60dB
Life of insertion and extraction:＞1000 times
3, Thunder-proof technical datasheet
The grounding device is isolated with the cabinet, isolation resistance is less than 2×104 MΩ/500V(DC)；
The withstand voltage between grounding device and cabinet is no less than 3000V(DC)/min, no puncture,no flashover；U≥3000V
Table 1 Model and configuration
|Model||Description||Size(Pic 1)A*B*C(mm)||Max Capacity|
|Into the largest cable diameter (mm)|
Cable outlet size
Drill 4 holes over the wall based on the size in table 1,place the expansion bolt Φ7.5*40,place the box to match up the holes and use bolt to fasten.
Fix 1 set of the easy pole ring to the telecom pole .
1. Users' Manual*1.
3. Accessories Bag * 1
4. Easy pole ring*2,M6*20mm Bolt*2(Option)
Packing, transportation and storage
This equipment packaging is moisture-proof and earthquake-proof. The accessories are packed first plastic
bags, then into the boxes with plastic bags for sealing. There are moisture-proof and earthquake direction signs
outside the boxes.
It can’t be inverted in the transport and be free from rolling when carrying. Please load carefully and
prevent the collision. You should prevent it from heavy rain before installation. The temperature in the
transport should be controlled between-35℃ to +55℃.
The excessive accumulation of goods should be stored on the cartons. The treasury should away from the
erosion of corrosive gas equipment and the temperature should be below 45℃ and higher than -5℃, and
relative temperature should not be high in long-term(generally less than 75%).